** The BAYweb App for iPhone, iPad, and Android phones and tablets, is now available. This initial version features remote monitoring, control, set point adjustments, and changing selected settings. It supports the Web Thermostat, Web Relay, and Web Integrator devices.
For iPhone and iPad users, go to the App Store and search for "BAYweb".
For Android phones and tablets using Google Play search for "BAYweb" or you can use this Link to go directly to the App. Note that there is also pre-release version of the App called "BAYweb Mobile", that will be discontinued soon. Make sure you install the released version.
Note the BAYweb mobile portal (www.bayweb.com/mobile) will be removed on June 1st, so install the App before then to use BAYweb from your phone.
Call or Email for quantity discount!
How it Works
The BAYweb internet thermostat system uses two modules. A simple keypad is placed where the old thermostat went. The BAYweb control module is installed behind the scenes, often in the mechanical room. 4-conductor thermostat wire runs from the keypad to the control module. 4-conductor thermostat wire (or up to 8 wires on the Advanced and Professional module) runs from other side of the the control module to your HVAC system. The control module plugs into a standard 115V electrical outlet, but can also be powered using 24V transformer from your HVAC equipment. A Cat5 ethernet cable runs from a LAN port on the control module to your internet router or switch.
Bay's Plug-N-GoTM networking technology enables you to utilize all of the Internet-based capabilities by simply plugging it in to your network. No network or router changes, or network experience is required.
Requires a full time broadband Internet connection. To use existing thermostat cable, at least 4 conductors are required. Exclusively for use in the United States. Temperature indicated in degrees Fahrenheit.
Setup is quick and simple. Use the Portal on BAYweb's website to set up your account. Once that is complete, setup your schedule, energy monitoring, keypad lockout, etc. on the internet from any computer with web access.
Wiring Requirements and Model Information
Please check thermostat wiring and terminals. If they are marked as follows and have wires connected to the terminals as noted.*
* Your thermostat may have additional terminals that are not being used. If there is no wire attached to a terminal, and no jumper to another terminal, please ignore these terminals when choosing a thermostat.
** Unit requires 4 wires. You may need to install a new thermostat cable - please consult if you are unsure. (It is possible, but not preferred, to obtain satisfactory service wiring using 3 wires - please consult if you are unsure.)
Please note that in rare cases, a manufacturer may use proprietary controls that may not be compatible with this thermostat.